Load carefully. Plan wood load based on BTU requirement. Maintain intense burns for
Remove ash regularly as directed.
Watch for soot build up in Flue pipe, and Heat Exchanger.
Realize the danger of extreme overheating due to over firing.
Danger of flue fire if poor maintenance produces creosote buildup.
Operation of unit during power failure, (i.e. manual operation of zone valves and flow check
When shutting down for extended periods, clean unit thoroughly.
BEFORE RELOADING THE BOILER WITH WOOD, DRAFT CONTROL FAN MUST BE
STOPPED, AND FLUE DAMPER FULLY OPENED FOR AT LEAST ONE MINUTE BEFORE
OPENING THE LOADING DOOR TO REFUEL.
This is necessary to ensure that smoke and flames from the fire will not exit the loading door and harm