Blade Size, Dia.
5,000 sq. ft.
3,025 sq. ft.
56” & 60” SPRAY PROOF CEILING FANS
MODELS 5610-1 AND 6010-1
56” & 60” AGRICULTURAL CEILING FANS
MODELS 5611-1 AND 6011-1
READ INSTRUCTIONS CAREFULLY BEFORE ATTEMPTING TO ASSEMBLE OR SERVICE THE LEADING EDGE
CEILING FAN. FAILURE TO COMPLY WITH INSTRUCTIONS COULD RESULT IN PERSONAL INJURY AND/OR
RETAIN FOR FUTURE REFERENCE.
General Safety Information
W A R N I N G : D I S C O N N E C T P O W E R B E F O R E
INSTALLING OR SERVICING THIS EQUIPMENT.
1. Mount 56” fans so that fan blades are 7 feet or higher
above the floor. Mount 60” fans so that blades are 10
feet or higher above the floor.
WARNING: DO NOT USE IN AN EXPLOSIVE
2. All electrical wiring should be done by a qualified
electrician in accordance with applicable National
Electrical Code and local electrical codes.
3. Make sure hanger hooks are mounted securely to
structural ceiling members.
4. Do not allow moving blades to come in contact with
any part of the body.
5. Make certain that the ground wire is connected to the
ground terminal and to a suitable electrical ground.
NOTE: When mounted in cathedral ceilings, the blade tip
should be at least 12 inches from the angled roof line to
prevent air “blow-back” causing possible fan sway.
CAUTION: Read and follow instructions carefully.
Failure to comply with instructions could result in
the risk of fire, shock, and injury to persons.
WARNING: TO REDUCE THE RISK OF PERSONAL
INJURY, DO NOT BEND THE BLADE BRACKETS
WHEN INSTALLING THE BRACKETS OR CLEANING
THE FAN. DO NOT INSERT FOREIGN OBJECTS IN
BETWEEN ROTATING FAN BLADES.
RECOMMENDED MOUNTING HEIGHTS
This fan is pre-assembled with a one foot long down rod
which is suitable for both heat reclamation in the winter
and warm weather cooling in the summer.
WARNING: ALL CEILING FANS SHOULD BE IN-
STALLED BY QUALIFIED PERSONNEL.
CAUTION: 56” fan should not be mounted lower than
7 feet from the floor. 60” fans should not be mount-
ed lower than 10 feet from floor.
The Leading Edge agricultural ceiling fans are designed
as a dual purpose product. By minimizing temperature
stratification in winter, they can reduce heating costs by
bringing trapped hot air to the floor. The summertime
application provides a gentle downward movement of air
for general air recirculation and evaporative cooling. A
permanent split capacitor motor and permanently
lubricated sealed ball bearings add to the efficiency and
quietness of the fan.
1. Remove fan components from carton carefully.
2. Check for shipping damage.
3. Check for any missing parts against parts list.
ASSEMBLY INSTRUCTIONS & PARTS MANUAL FOR